Flint and Walling Water Well Submersible Pumps, Centrifugal and Self Priming Sprinkler Pumps, Jet Pumps and Water System Accessories are all available from Dean Bennett Supply where we welcome the Do-it-yourself installer. Call 1-800-621-4291 to select your well supplies.
Plumbing manifold sold separately
Constant Pressure manifold, with 3/4" brass
boiler drain, 100 psi pressure gauge, and 100 psi pressure relief
Constant Pressure manifold only $ 59.50
#020627 CP75 Pressure Sensor Switch Kit $ 97.00
is pictured the constant pressure manifold mounted to the CP bracket
DEAN BENNETT SUPPLY COMPANY
operates similarly to the cruise control on your car. Once the speed is
set, the engine is electronically controlled to maintain that speed. The F&W system
maintains a constant pressure so there is no more pressure cycling between 30 psi, 40 psi
and 50 psi from your well pump. When more water is required, the pump runs faster, and
when less water is needed, the pump runs slower.
The electronic controller provides diagnostics against a variety of typical application hazards. You are protected against Rapid Cycling or water logged tank problems, short circuit to motor, under voltage, pump overload caused by clogging with sand or silt, and from running dry.
NOTE: Per Franklin Electric, the wire distance from the CP controller to the motor should not exceed 1000 feet in distance.
How does the constant pressure water system work?
The CP SubDrive Water Controller is the heart of the system. As water passes through the water line, the water pressure is sampled several times a second by the pressure controller which signals a microprocessor to control the pump, by speeding up or slowing down the motor, much like your cruise control on your car works. The controller is factory set at 50 psi, and can be adjusted to a range of 30 psi thru 70 psi, with the turn of a screw located inside the pressure switch controller.
What are the benefits of the Constant Pressure Pump?
The Commander Pro series provides steady
"city-like" water pressure, which does not fluctuate like normal rural well systems do.
Do Not use a GFCI (Ground Fault Interrupter) with a SubDrive
Do not use of a GFCI on a SubDrive Controller will cause the GFCI to trip on start up and the motor will not run.
DEAN BENNETT SUPPLY CO.
F&W CONSTANT PRESSURE PUMPS QUALIFY TOWARD OUR $